- , Unit/Units
- Pure Water
- Drinking Water Plant
- Semi Automatic
- Stainless Steel
- 400-440 Volt (v)
Raw Water Treatment:Raw water source should be well protected, available easily, un-contaminated, like - Bore well water Line, Closed Ring Well, Municipal Supply Line or Other source where treatment is possible.
Raw Water Storage Tank:Water is transferred to Raw Water Storage Tanks using proper pumping system and un-contaminating piping work.
Raw Water Feed Pump:Either Submersible Pump or surface mounted Centrifugal pump can be used with good quality UPVC or CPVC or SS piping can be used for this application.
Multigrade Sand Filter:Water is passed through Multi Media Filter with the help of Feed pump of suitable capacity to remove suspended impurities.
Activated Carbon Filter:Activated Carbon Filter removes excess chlorine (de-chlorination), odour, colour and turbidity due to colloidal suspended impurities and organic impurities.
Anti Scalant Dosing Pump:De chlorinated water is then dosed with Anti Scalant Solution to avoid scale formation on the membrane.
Micron Cartridge Filter:Water is further passed through 10-micron cartridge filter to remove micron particles to avoid clogging of the RO membrane and to improve the silt density index.
High Pressure Pump:The pump supplies the pressure needed to push water through the membrane, even as the membrane rejects the passage of salt through it. It requires a large amount of energy.
Reverse Osmosis System:Reverse Osmosis unit will reduce the dissolved Salts up to 95% of the In feed TDS.
pH Dosing System:Liming material is used to adjust pH between 6.8 and 8.1 to meet the potable water specifications, primarily for effective disinfection and for corrosion control.
U.V. System:The water runs through a UV system just before dispensing from the faucet for 99.99% destruction of bacteria, virus & protozoan cysts.
Ozonation:Raw water is Ozonated to oxidize the organic impurities that kill bacteria and virus.
Product Water Storage Tank:Treated water from RO unit will be stored into SS tank.
Micron Cartridge Filter:This treated water is then passed through 0.2 micron cartridge filter before it is taken for the filling.
Filling Section:Finally the treated is ready to be filled in bottles, jars, glasses or pouches.
Laboratory testing as per ISI standard:
Treated water is tested using IN HOUSE Water Testing laboratory Where Chemical and Micro Biologically Water is tested for Chemical and Micro Biological parameters. For this, a complete full fledge Water Testing CHEMICAL and MICRO BIOLOGICAL Lab is required. However, water is also tested for Pesticide and Radio-nuclear parameters in outside Bureau of Indian standards approved laboratory.
To be provided by Client:
Three phase power supply for RO and other machinery
For Raw water (RCC Or PP)
As require for RO Plant.
Water Analysis Facility
Water analysis for raw water and final water.
As and when require
Anti Scalant and other chemicals as require.
For waste water from RO Plant.
For foundation for RO and other machine.
- 100 Per Week
- 10 Days
- Asia, Middle East
- All India
4, Gopal Nagar, Nandida Char Rasta, Bardoli Surat Gujarat India 91-2622-222755